Kilovault Solar Lithium Batteries - KiloVault® is dedicated to offering innovative and reasonably priced renewable vitality options for residential and business functions.
KiloVault® design, market, and promote power storage and power conversion merchandise based on modern technologies, that cut back the price of entry for householders, and help cut back the impression of humanity on the environment.
Kilovault Solar Lithium Batteries
KiloVault® has more than 20 years of expertise designing renewable vitality techniques. Our founders and lead growth engineers have unique insight into the wants of the residential power. This is just their latest concept to assist clients retailer the solar, and save the planet.
Kilovault Solar Lithium Batteries - KiloVault® Solar Energy Storage merchandise cover a wide range of applications, including Flexible Energy Storage, Wall-Mount Energy Storage, and Portable Emergency Power.
1. KiloVault HLX Series
KiloVault HLX-Series Deep- Cycle Lithium Batteries offer a configurable approach to residential energy storage wants. The HLX Series can be utilized individually or in combination for 12, 24, or 48-volt systems, with storage capacities ranging from 150 Amp-hours to 1,200 Amp-hours.
KiloVault HLX Series Features:
- Flexible – Works in 12, 24, or 48V configurations
- Gives You More- You can use the complete battery’s capacity, discharging it 100%
- Long-life- Even after discharging it completely 2000 occasions, 80% of the capability remains.
- Maintenance Free – No watering required, or cleaning of hazardous chemical compounds
- High Efficiency – Giving you up to 12% extra use-able stored vitality
- Smart Investment – Lower value per watt-hour/cycle and an extended lifespan than lead batteries
- Safer – No thermal run-away points as with other lithium applied sciences
- Heavy Duty -Takes as much as 150A of steady charging/discharging current, assembly the robust demands of significant inverters and chargers
- 7.5 Year Warranty
KiloVault HLX Series Product Specifications:
|1200 HLX||1800 HLX||3600 HLX|
|Rated Voltage||12.8 V DC||12.8 V DC||12.8 V DC|
|Nominal Amp-Hour Capacity||100Ah||150Ah||300Ah|
|Continuous Discharge Current||100A||150Ah||150Ah|
|Maximum Discharge Current||100A||150Ah||200A for 30 min, 150A (steady)|
|Max Charge Current||80A||150Ah||150Ah|
|Peak Discharge Current < 3 secs||350A||500A||500A|
|Length||12.5 in (318 mm)||19.1 in (485 mm)||20.5 in (520 mm)|
|Width||6.5 in (165 mm)||6.7 in (170 mm)||8.7 in (220 mm)|
|Height||8.5 in (215 mm)||9.4 in (240 mm)||10.6 in (269 mm)|
|Battery Weight||27 lbs (12.2 kg)||41.7 lbs (18.9kg)||84.4 lbs (38.3 kg)|
|Shipping Weight||30 lbs (13.6 kg)||45.2 lbs (20.5kg)||103.4 lbs (46.9 kg)|
KiloVault 1800 HLX
2. KiloVault RES-Q
KiloVault RES-Q Portable Emergency Power Unit features a 1,200 Watt-Hour battery, charge controller, and inverter that can power a refrigerator and charge cell phones. The KiloVault RES-Q is designed to be charged by solar panels, a backup generator, or commonplace 120 VAC energy, and will provide as much as 1200Wh of emergency backup energy.
KiloVault RES-Q Features:
- 1500W Pure Sinewave Inverter
- 1200Wh KiloVault Lithium Battery
- 25A Solar Charge Controller
- Built-in AC Charger
- Liquid Crystal Display Status
- 2x 120V Outlets
- 1x 12V Cigarette Lighter Adapter
- Lead Acid Battery Expansion Port
KiloVault RES-Q Specifications:
|Rated Energy Capacity (Watt Hours)||1280 Wh|
|DC Voltage Nominal||12.8V|
|Nominal Amp-Hour Capacity||100 Ah|
|Cycle Rating||2500+ cycles @ 80% Depth of Discharge|
|Minimum Charge Time||2.5 Hours|
|Charge Retention||1 Year (85%)|
|Integrated Inverter||1500W steady output/120VAC pure sinewave/Slow begin function protects inverter from over-current draw|
|Maximum Charge Current||15A @ 12V from AC or DC circuitry|
|Maximum DC Output||20A|
|Operating Temperature||23 – 111°F (-5 – 45°C)|
|Surge Ratings||3000W (5ms), Soft Start (for brief surges)|
|Environmental Rating||Indoor rated only - not rated for rainy, damp, snowy situations|
|Expansion Port for External Battery||We highly advocate using an LFP battery (ie. KiloVault). The RES-Q completely discharges the exterior battery, down to 10.5V, earlier than switching to the internal battery. Completely discharging a lead-acid battery will likely harm it and permanently reduce its capability.|
|Warranty||2 Year Limited|
|Length||18.9 in (480 mm)|
|Width||9.4 in (238 mm)|
|Height||15.7 in (400 mm)|
|Weight||61.7 lbs (28 kg)|
KiloVault RESQ 1500
KiloVault HLX Tips And FAQ
Is it good to insulate the KiloVault battery?
It's the same with any type of battery. Because batteries warmth up after they charge, should you insulate the field they're in, it's going to retain the heat better and the batteries will stay hotter. But make certain to take away the insulation within the sizzling months, as overheated batteries could have a shorter life.
What is the perfect working and storage temperature for the KiloVault?
The optimal temperature range overall is 59 – 95°F (15 – 35°C). Full operating temperatures have to be larger than 32°F (O°C) and fewer than 133°F (45°C). Charging the battery under 32°F (0°C) will potentially harm it.
What are the really helpful charge controller/inverter settings?
We highly advocate setting the Bulk/Absorb voltage to *14.0V* for a 12V system (*28.0V* for 24V system, *56.0V* for 48V), float voltage of 13.8V (27.6V for 24V, 55.2V for 48V). Higher settings will scale back the *life* of the batteries. For the inverter low voltage cut-off we strongly suggest 12.0V *or higher* (24.0V, for 24V systems, 48.0V for 48V programs). Limit the length of the soak up voltage interval to 2 minutes if the charger is greater than 100A, otherwise set to 5 minutes.
Are there any issues when wiring the batteries in parallel?
Yes - for the HLX collection batteries, the utmost configuration is 4 parallel strings of 4 sequence batteries (16). In addition, when including one other parallel row of batteries to an current one, you will need to preserve all parallel sequence strings within 0.2V of one another. Before including a new row of batteries to an current one, charge all batteries to 100% first.
For the CHLX sequence batteries, a maximum of 4 batteries can be utilized in sequence or parallel, but NOT each. The CHLX are programmed in order that when they're in parallel or collection if one gets chilly enough to begin heating, the entire CHLX in collection or parallel will begin heating. This is to stop broadly totally different energy attracts and states of charge in the battery bank when some are heating and can't charge, while others are warm enough to charge. As the communication between the CHLX happens via the power cables, if related this fashion, this communication can not happen.
Can I mix and match models or brands?
No - this isn't good apply with any battery bank.
Should I do an equalization charge on the batteries?
No- much like AGM batteries, an equalization charge may damage them by overcharging them.
Are the batteries shipped fully charged, or do I must charge them?
No - shipping pointers don't enable deep cycle batteries to be absolutely charged throughout shipment. **Before you set the batteries into operation they must ALL be charged to exactly the identical voltage (select a voltage between 14.0-14.4, V but be certain that they're *ALL* the identical). This will ensure you start with an excellent charge throughout the battery financial institution. Suggested battery charger (cables not included with this charger but can be found - use merchandise code ALTCC-6AWG-60RB). We do NOT recommend utilizing the Iota IQ-LIFE PO Smart Charger accessory for use with KiloVault batteries as a result of the charge voltage is simply too excessive.
Can I do a continuing trickle charge on the batteries?
Storing the batteries with a relentless small trickle charge shouldn't be really useful. Unlike lead-acid batteries, lithium iron phosphate batteries self-consume power at such a low rate (0.020 amps or about 6 Watt-hours/day), the battery will be simply over-charged if put on a trickle charger. Over-charging the battery triggers the over-charge protection - shutting it down till the voltage goes down sufficient by itself. Once that occurs the trickle charger would shortly increase the voltage up too high once once more. As a end result, the fixed cycling of this circuitry will shorten the lifetime of all the battery.
Is it bad to overcharge or over-discharge the battery?
Yes, it will lower the life of the battery. It’s really helpful to by no means discharge or charge the battery to the point where it has to close down to guard itself.
Kilovault Solar Lithium Batteries - I have been operating my new system with the KiloVault 3600 HLX for two weeks and it works unbelievable. I've watched it put out 168 amps with no challenge and only a couple tenths drop in voltage while doing it after which instantly returns to the normal 13. 3 volts.
I've seen it charge very quickly at 68 amps from my solar array. The solely concern I've had is that the BMS will put this battery on standby when my PV input matches the load on the battery... the complete system "pauses" causing the inverter to shut off, the charge controller goes to relaxation, or to alarm and the 12-volt system goes dead for a couple of seconds... Be advised the battery can go on standby...